Integrity Comfort Solutions has provided top quality heating and ac repair services in Spring, TX since 1980.
What makes our heating and ac repair top quality? Read our Spring, TX reviews to see why.
for Spring, TX
Our Reviews by City
Honest and thorough service
JJ Hollie - Spring, TX
Hruby - Spring, TX
Garcia - Spring, TX
Ken is a very professional and caring technician that obviously enjoy what he does. He takes time to explain his findings in a simple and clear way, yet without pushing customers to buy products on the spot. He makes sure customer’s concerns are heard and with kindness and respect he tries to provide possible solutions. He is very clean and considerate when doing his job,taking the necessary time to do a thorough inspection with the reliability that should be.
Stanley - Spring, TX
Gutierrez - Spring, TX
LEE - Spring, TX
Integrity’s service is professional, thorough and they always arrive on time or before the appointment time.
MIKE - Spring, TX
We are very happy to have had Israel, work on our AC system. He was able to diagnose the problem, offer solutions and later came back with the repair fix. AC system is back in operation.
KEVIN - Spring, TX
Great Employees, Great Service
Pat - Spring, TX
Justin is very helpful and professional. I have used Integrity Comfort Solutions for almost 3 years now and am always more than satisfied with the quality of service and the friendly, helpful employees.
Todd - Spring, TX
David and his crew were excellent!
After hours call for no heating in downstairs system. Located furnace in the attic space in the garage for the downstairs system. Found a bad run capacitor as well as a clogged drain line and no float switch in the pan. Corrected the issues at a reasonable price.
No heat call - woodlands
Fall heat inspection in the woodlands
Found a crack in a heat exchanger on a furnace dated 1991.
Performed heat inspection to ensure all equipment is working safely and properly.
Cleaning a furnace Ignitor and furnace restart
Turned on switch on 24V gas valve and recycled power, set both zones at 72 degrees and verified operation.
Performed annual heat inspection
Performed heating maintenance, system working great
Had a no cooling call. Found a bad run capacitor, compressor was still coming on due to the hard start kit that was installed to the condenser, customer noticed the downstairs was not cooling and called us for a solution. Repair was made and after a full evaluation of the system in the cooling mode, suggestions were made to add more return air to downstairs system to allow for better air circulation.
Performed fall inspection on HVAC system to ensure everything is working properly
GAS FLEX LINE TO CORRECTLY RUN THE GAS LINE ON THE FURNACE
HEAT INSPECTION/ CHECK HUMIDIFIERS
DRAIN LINE ISSUES/FILTER ISSUE
SYSTEM NOT HEATING
WATER COMING THROUGH CEILING BY HVAC EQUIPMENT
HEAT INSPECTION/EST FOR DUCT CLEANING
STILL HAVING ISSUES OVER FIRING CAUSING BREAKER TO TRIP
SYSTEM IS NOT HEATING